GB 30 000 053 - 2 Wireless sensor Smoke alarm FRW-ws Only skilled electricians may install this electrical equipment otherwise there is the risk of fire or electric shock! Wireless smoke alarm Detectomat HDv 3000 OS, white, with wireless transmitter module inserted. Only 0.03 mW standby loss of the wireless transmitter module. This battery-powered smoke alarm is a reliable device that generates an alarm in case of fire by visual detection based on the scattered light principle. Certified to EN 14604:2005 by the VdS (German independent testing institution). Alarm signal produces loud tone at intervals of 0.5 second. Operation indication every 40 seconds by flashing red LED. Fault and battery change display by short alert tone every 40 seconds. In case of an alarm, the inserted wireless transmitter module transmits an NO contact telegram to the Eltako wireless network. This also takes place when the test button is pressed. While the alarm sounds, the telegram is repeated every 10 seconds. Power consumption during an alarm is 23 μA from a fitted 9 V lithium battery that powers the smoke alarm. As soon as the alarm is cleared, 2 button NC contact telegrams are sent at an interval of 400 ms. Every 20 minutes, a button NC contact telegram is sent as status telegram. If the battery voltage is less than 7.2 V, a battery status telegram is sent in addition. It can be taught into an actuator in the same way as the upper NO contact of a left double-switch rocker. A single FRW-ws can be taught in actuators FSR12, FSR61, FSR70, FZK12, FZK61 and FZK70. Several FRW-ws devices can be taught in the FZK actuators. By logic linking, alarm end is only signalled when all FRW s de ices send no more alarms alarm end is only signalled when all FRW-ws devices send no more alarms. Battery life cycle of 9 V lithium approx. 6 years, 9 V alkaline approx. 3 years. A lithium battery is contained in the scope of supply. Teaching-in smoke alarm in actuators or GFVS software: Actuator FSR..: set to 'Teach-in universal button' ('Button on/off'): press test button of the FRW. As soon as the warning tone sounds, release the test button. After teach-in, set the actuator to the ER (without EW time) function. Actuator FZK12: set the middle rotary switch to LRN. Press test button of the FRW. As soon as the warning tone sounds, release the test button. After teach-in, set the the middle rotary switch to AUTO 2 and the top and bottom one to 0. Actuator FZK61: set the bottom rotary switch to 0 and the top one to LRN. Press test button of the FRW. As soon as the warning tone sounds, release the test button. After teach-in, set the top rotary button to 0. Battery types (for detectors with wireless modules we recommend lithium batteries) Approved battery types: FDK CP-V9J, Ultralife U9 VL-J / -P, Panasonic Power Alkaline 9 V, Varta 4022 Alkaline 9 V, AlkalineXtreme 6LR61 9 V. Changing batteries: AlkalineXtreme 6LR61 9 V. 1R th k l f th Changing batteries: 1. Remove the smoke alarm from the base by turning it anticlockwise. 2.Connect the new battery to the smoke alarm (ensure correct polarity!) and insert it in the battery compartment provided. 3.Place the upper part containing the new battery onto the base and fix it by turning it clockwise. 4.Check whether the LED flashes. 5.Carry out a function test by pressing the light transmission bar for at least 1 second. 6.When the device passes the function test, an alert tone sounds. The smoke alarm is working properly. If no signal sounds, the device is not in working order. Then replace the battery and carry out the function test again. If the alert tone sounds again, the smoke detector is defective and must be replaced by a new one. Technical data Detection principle Tyndall effect (optical) Visual alarm display optic (red LED) and acoustic alert tone >85 dB(A)/3 m Regulations fulfilled Operating voltage (DC voltage) Operating temperature Max air humidity Max monitoring area Max air velocity Response sensitivity typical Protection class Weight approx. Dimensions with base max. (dia x H) VdS Approval No EN 14604:2005 9V ! Caution: Exchange batteries properly, otherwise there is a risk of explosion. Replace with an equivalent approved type. -10°C to +60°C 95% 60 m² up to 6 m hight 20 m/s 0.15 dB/m IP 40 150 g 100x55 mm G202042 The crossed out waste bin symbol indicates that the product may not be disposed of in the domestic or business waste. It should be separated from refuse so that valuable resources can be recycled. After use, batteries can be returned free of charge to the point of sale. ! The crossed out waste bin symbol indicates that the product may not be disposed of in the domestic or business waste. It should be separated from refuse so that valuable resources can be recycled. After use, batteries can be returned free of charge to the point of sale. Caution: Exchange batteries properly, otherwise there is a risk of explosion. Replace with an equivalent approved type. ELTAKO GmbH hereby declares that the products that relates to this operating manual, are in compliance with the essential requirements and other relevant provisions of directive 1999/5/EC. A copy of the EU declaration of conformity can be requested at the address below. Must be kept for later use! Eltako GmbH D-70736 Fellbach +49 711 94350000 www.eltako.com 31/2014 Subject to change without notice.
© Copyright 2018 ExploreDoc