Fire Control Panels UL, ULC, CSFM Listed; FM, NYC Fire Dept Approved* Automatic Extinguishing, Deluge and Preaction Sprinkler System Releasing Control Features Releasing control using the Simplex® 4010ES Fire Alarm Control Panel to provide: Coverage for multiple areas of Automatic Extinguishing Release and/or Deluge and Preaction Sprinkler System Release including audible escalation of events Control of compatible Listed/Approved 24 VDC automatic control actuators, one per circuit; or two 12 VDC actuators in series per circuit Releasing appliance circuits (RACs) by connecting Notification appliance circuits (NACs) to Suppression Release Peripherals for actuator supervision and control Four, 3 Amp Notification Appliance Circuits (NACs) in the panel for use with Suppression Release Peripherals (SRP) and required notification appliances Additional actuator circuit control and additional NACs are available using 4009 IDNet Addressable NAC Extenders and Suppression Release Peripherals Audible Escalation of Events: Temporal or 20 bpm March Time pattern for first cross-zone alarm 120 bpm March Time pattern indicates releasing timer active On steady indicates releasing timer expired and actuator is activated NOTE: Requires NACs dedicated to conventional horn control (not SmartSync operation) with strobes controlled on separate NACs Actuator Actuator Control Circuit Agent discharge path Agent source Coil supervisory module COILSUPERVISIONMODULE( 2AMP) 2081 - 9046 INST ALLATION INSTRUCT IONS574- 437 REV MAINTAIN1/4 " SEPARATION BETW EENPOW ERLIMIT ED ( RED/BLK) ANDNONPOW ER LIMIT ED( YEL/BLK) W IRING RED NAC+ DATECODE: NACBLK 519- 9 58 YEL S BLK S IMP L E X T IM E R E C O RD E R CO .G A R D N E R MA .U S A Release appliance circuit Maintenance Disconnect Switch (with indicator lamp) Suppression Release Peripheral NORMAL 0 1 DISC./ DISABLE FIRE SUPPRESSION DISCONNECT / DISABLE FIRE RELEASING DEVICE Typical addressable initiating devices Power for indicator lamp (if required) IDNet communications FIRE SUPPRESSION SYSTEM ABORT - I DN ET + ID NET IN + IN - Dedicated NAC circuit PUSH AND HOLD MANUAL RELEASE 4009 IDNet NAC Extenders provide: Up to eight NACs for notification requirements and for NAC input to Suppression Release Peripherals Control is via IDNet addressable communications SUPPRESSION RELEASE PANEL 4090-9005/-9006 Suppression Release Peripheral (SRP) with Dual Command Control: Dual command control requires that both IDNet communications commands and an activated NAC are present to initiate the desired release NAC provides wiring supervision to the actuator including monitoring of coil continuity and short circuit supervision to the coil supervision module Suppression Release Peripheral control features: An on-board DC-DC regulator compensates for voltage drops to the peripheral and ensures proper control circuit voltage over a wide operating range Provides a single RAC for control of actuators for up to 2 A using a 3 A NAC input (1 A using a 2 A NAC input) Related system components: 4010ES Series control panel with Releasing Appliqué Dedicated NAC output from 4010ES (or compatible NAC Extender) Coil supervision module, one per RAC Maintenance Switch, one per RAC Abort Switch connected via an addressable interface module UL listed to Standard 864 CAUTION: This Control Unit has been arranged for releasing service. Disable all releasing device circuits prior to servicing. 4010ES Control Panel with Suppression Release Appliqué 4010ES Release Control Simplified Block Diagram Introduction When combined with Suppression Release Peripherals, the 4010ES series fire alarm control panel provides actuator supervision and control for use in automatic extinguishing, and deluge or preaction releasing systems. Hazard area initiating and notification devices are controlled using either conventional or addressable circuits per standard 4010ES capabilities. The necessary releasing system logic is implemented within the 4010ES control panel as required for the local application. * This product has been approved by the California State Fire Marshal (CSFM) pursuant to Section 13144.1 of the California Health and Safety Code. See CSFM Listings 7165-0026:0369 and 7300-0026:313 (SRP) for allowable values and/or conditions concerning material presented in this document. It is subject to re-examination, revision, and possible cancellation. NYC Fire Dept COA #6095. Additional listings may be applicable; contact your local Simplex product supplier for the latest status. Listings and approvals under Simplex Time Recorder Co. are the property of Tyco Fire Protection Products. S4010-0005-3 2/2012 Automatic Extinguishing Release Systems Releasing System Requirements (Continued) These systems automatically activate electrically controlled actuators for the release of a fire extinguishing agent (such as dry chemical, water spray, foam, CO2, or clean agent) in response to fire detection device inputs as determined by programming of the host fire alarm control panel. 5. FM Approved Automatic Extinguishing Release requires secondary standby to be a minimum of 24 hours with 5 minutes of alarm. Actuators must be electrically compatible. 6. FM Approved Deluge and Preaction Sprinkler operation requires that: initiating device circuits be Class A and wired to Listed/Approved devices; standby power capacity must be a minimum of 90 hours with 10 minutes of alarm; and that compatible Automatic Water Control Valves must be used. (Refer to actuator list on page 7.) Automatic Extinguishing Release System Panels are required to have a minimum of 24 hours of standby power. Initiating devices must be Listed/Approved for the application, and may be wired either Class A or B. Control actuators must be electrically compatible with the control panel circuits and power supplies, and are wired Class B to provide coil supervision. 7. Maintenance Switches, one per RAC, are required per NFPA 72, the National Fire Alarm and Signaling Code (2002 Edition, Chapter 6) to allow the system to be tested or serviced without actuating the fire suppression systems. Their use may not be allowed in some jurisdictions, always confirm local requirements. When used, Simplex Maintenance Switches are required to ensure that operation initiates a supervisory condition. Deluge or Preaction Sprinkler Systems These systems automatically activate water control actuators in response to fire detection device inputs. Deluge Sprinkler Systems employ open sprinkler heads and provide water flow when the fire detection system activates a common automatic water control actuator. They are used to deliver water simultaneously through all of the system sprinkler heads. This type of system is applicable where the immediate application of large quantities of water over large areas is the proper fire response. 8. Abort Switches are available when abort operation is required. When used, connect to an addressable Supervised IAM model 4090-9001 or similar addressable adapter module. The Simplex abort switch and the IAM mount in a single gang box, 2-1/2” minimum depth. Preaction Sprinkler Systems are similar to deluge systems except that normally closed sprinkler heads are used and supervisory air pressure is maintained in the pipe. Operation requires both an activated sprinkler head and an activated fire alarm initiating device with specific programming determined at the host fire alarm control panel. 9. Addressable Manual Releasing Stations are used to initiate activation of the releasing actuators with the appropriate time delay implemented by the fire alarm control panel. 10. Notification Requirements. Each hazard area typically requires general audible and visible fire alarm notification and additional dedicated NACs for area releasing status notification. Suppression releasing is compatible with conventional panel mounted NAC modules as well as for use with the 4009 IDNet NAC Extender. Releasing System Requirements 1. Releasing actuators are controlled from a Suppression Release Peripheral (4090-9005 or 4090-9006). Connections are 2-wire, Class B releasing circuits with only one 24 VDC actuator per circuit. Where applicable, two, 12 VDC actuators in series, or one 12 VDC actuator with manufacturer supplied resistor may be used. 11. Additional Suppression Release Peripheral Reference. Refer to Installation Instructions 579-385. Additional Releasing Systems Reference 2. Coil Supervision Module 2081-9046 must be wired electrically before the actuator and located in the actuator wiring junction box. (Refer to diagram on page 5.) The connected RAC provides continuity supervision of the actuator coil and wiring and provides short circuit supervision to the coil supervision module. 3. Cross-zoning or other alarm initiation logic per system requirements, is to be implemented by programming at the fire alarm control panel. 4. UL Listed Automatic Extinguishing Releasing operation requires that: battery standby must be a minimum of 24 hours with 5 minutes of alarm and that listed actuators are used, refer to list on page 6. For additional information, refer to Factory Mutual Research Corporation (FMRC) “FMRC Approval Guide,” FM Approval standard “Deluge Systems and Preaction Systems.” Please note that proper operation of releasing control systems requires that the system design, installation, and maintenance be performed correctly and in accordance with all applicable local and national codes, and equipment manufacturer’s instructions. No liability for total system operation is assumed or implied. 2 S4010-0005-3 2/2012 Product Selection 4010ES Releasing Control System Modules Model Description Reference 2081-9046 Coil Supervision Module Required, one per RAC, mounts in the releasing actuator wiring junction box; see specifications section for details 2080-Series* Maintenance Switches One per RAC; flush or surface mount; indicator lamp models require separate 24 VDC wiring 2080-9056* Flush mount 2080-9057* Surface mount Abort Switch As required, connects via an IDNet addressable interface module; mounted on a single gang stainless steel plate; installation requires a single gang box, 2-1/2” (64 mm) minimum depth * Refer to data sheet S2080-0010 for Abort and Maintenance switch details. Releasing Appliqués, Required for 4010ES Suppression Releasing Applications Model Description 4010-9830 English 4010-9830CAF French Suppression Releasing Appliqué; field applied (same appliqué as is used on the Simplex model 4010 Suppression Release Panel) Suppression Release Peripheral and Accessories Model Description Reference 4090-9005 Basic Suppression Release Peripheral on mounting plate Requires mounting box 2975-9227, ordered separately 4090-9006 Suppression Release Peripheral mounted in red box; required for ULC listing Includes LED indicator on front of door 2975-9227 Red mounting box; required for 4090-9005 4090-9812 Red LED IDNet communications indicator option kit; mounts on door of 2975-9227 box These items are included with model 4090-9006 Additional Product Data Sheet Reference Subject Data Sheet Subject Data Sheet Releasing System Abort and Maintenance Switches S2080-0010 Addressable Zone Adapter Modules S4090-0003 Addressable Manual Stations for Releasing Applications S4099-0002 TrueAlarm Sensors and Bases S4098-0019 Addressable Manual Stations for Standard Applications S4099-0001 TrueAlert Electronic Horns S4901-0010 4010ES Basic Control Panels S4010-0004 TrueAlert Non-Addressable Strobes (V/O) S4906-0001 Supervised IAM S4090-0001 TrueAlert Non-Addressable 4-Wire Horn/Strobes (A/V) S4903-0011 Contact your local Simplex product supplier for additional information on compatible IDNet addressable devices and TrueAlert notification appliances. 3 S4010-0005-3 2/2012 4010ES Releasing System One-Line Connection Reference with 4009 IDNet NAC Extenders 4090-9005/-9006 Suppression Release Peripheral (SRP) Horn and strobe NACs; 4 NACs standard, up to 8 NACs available FIRE RELEASING DEVICE Actuator Control Circuit Agent source Coil supervisory module NORMAL 0 1 DISC./ DISABLE RED NAC+ NACBLK COIL SUPERVISIONMODULE( 2AMP) 2081- 9 046 INSTAL LATIONINSTRUCTIONS574- 437 REV MAINTAIN1/4" SEPARATION BETW EENPOW ERLIMITED ( RED/BLK) ANDNONPOW ER LIMITED( YEL/BLK) W IRING DATECODE: YEL S 519- 958 BLK S IMP L E X T IME R E CO R D E R CO .G A R D NE R M A .U S A FIRE SUPPRESSION DISCONNECT / DISABLE Actuator (FM Approved water valves Group A, B, D, E, F, G, or H) Agent discharge path IDNet communications to up to 10 total 4009 IDNet NAC Extenders Dedicated NAC FIRE SUPPRESSION SYSTEM ABORT - I DNET IN + +IDNET IN - PUSH AND HOLD MANUAL RELEASE CAUTI ON DI SCO NNECT 4009 IDNet NAC Extender (if required) PO W ER BEFO RE SERVI CI NG 24 VDC for Maintenance Disconnect status indicator (if required) 4009 IDNet NAC EXTENDER TM IDNet communications IDNet communications Dedicated NAC wiring To SRP, either from 4010ES (dashed line) or from 4009 IDNet NAC Extender FIRE SUPPRESSION SYSTEM ABORT - IDNET IN + +IDNET I N - 4010-9830 Suppression Release Appliqué, to be applied in the field (also available in French with 4010-9830CAF): PUSH AND HOLD MANUAL RELEASE Supervised IAM with optional Abort Switch SUPPRESSION RELEASE PANEL CAUTION: This Control Unit has been arranged for releasing service. Disable all releasing device circuits prior to servicing. IDNet Addressable devices NAC for horn control SUPPRESSION RELEASE PANEL CAUTION: This Control Unit has been arranged for releasing service. Disable all releasing device circuits prior to servicing. NAC for strobe control Use separate NACs for horn and strobe control to implement audible escalation of events 4010ES Control Panel with Suppression Release Appliqué 4 S4010-0005-3 2/2012 Suppression Release Peripheral Wiring Reference Maximum Release Appliance Circuit (RAC) Wiring Distances from Suppression Release Peripheral to the Valve Solenoid (based on a total drop of 0.6 V) RAC Output Current (refer to solenoid rating) Distance 18 AWG 16 AWG Total Line Resistance 14 AWG 0.50 A 74 ft 23 m 118 ft 36 m 188 ft 57 m 1.06 0.75 A 50 ft 15 m 79 ft 24 m 126 ft 38 m 0.71 1.00 A 37 ft 11 m 59 ft 18 m 94 ft 29 m 0.53 1.25 A 30 ft 9m 47 ft 14 m 75 ft 23 m 1.06 1.5 A 25 ft 7.6 m 39 ft 12 m 63 ft 19 m 0.71 1.75 A 21 ft 6.4 m 34 ft 10 m 54 ft 16 m 0.53 2.00 A 19 ft 5.8 m 30 ft 9m 47 ft 14 m 0.53 2 2 2 Metric wire equivalents: 18 AWG = 0.82 mm ; 16 AWG = 1.31 mm ; 14 AWG = 2.08 mm NORMAL 0 1 DISC./ DISABLE FIRE SUPPRESSION DISCONNECT / DISABLE FIRE RELEASING DEVICE RED NAC+ NORMAL 0 1 DISC./ DISABLE COIL SUPERVISIONMODULE( 2 AMP) 2081- 9046 INSTALLATIONINSTRUCTIONS574- 437 REV MAINTAIN1/4 " SEPARATION BETW EENPOW ERLIMITED ( RED/BLK) ANDNONPOW ER LIMITED( YEL/BLK) W IRING DATECODE: NACBLK FIRE SUPPRESSION DISCONNECT / DISABLE YEL S 519- 958 BLK S IM P L E X T IM E R E C O R D E R C O .G A R D N E R M A .U S A FIRE SUPPRESSION SYSTEM ABORT - IDNET IN + +IDNET IN - PUSH AND HOLD MANUAL RELEASE Maximum Notification Appliance Circuit (NAC) Wiring Distances to a Suppression Release Peripheral (0.5 A to 1.75 A drop is based on a total drop of 3.4V; 2 A drop is based upon a total drop of 1.2 V) RAC Output Current (refer to solenoid rating) Distance 18 AWG 16 AWG Total Line Resistance 14 AWG 0.50 A 250 ft 76 m 399 ft 122 m 635 ft 194 m 3.58 0.75 A 167 ft 51 m 266 ft 81 m 423 ft 129 m 2.39 1.00 A 125 ft 38 m 199 ft 61 m 317 ft 97 m 1.79 1.25 A 100 ft 30 m 159 ft 48 m 254 ft 77 m 1.43 1.5 A 84 ft 26 m 133 ft 41 m 212 ft 65 m 1.19 1.75 A 72 ft 22 m 114 ft 35 m 181 ft 55 m 1.02 2.00 A 25 ft 7.6 m 39 ft 12 m 63 ft 19 m 0.36 2 2 FIRE SUPPRESSION SYSTEM ABORT PUSH AND HOLD 2 Metric wire equivalents: 18 AWG = 0.82 mm ; 16 AWG = 1.31 mm ; 14 AWG = 2.08 mm 5 S4010-0005-3 2/2012 Specifications Suppression Release Peripheral 4090-9005 and 4090-9006 Communications RAC Output Rating IDNet, one address with 4010ES 2 A maximum with 4009 IDNet NAC Extender 1 A maximum NAC Power Requirements NOTE: 4010ES NACs are rated at 3 A; 4009 IDNet NAC Extender NACs are rated at 2 A, Extender expansion NACs are rated 1.5 A At nominal 24 VDC, regulated; refer to NAC Power Requirements for more detail Voltage 16 to 32 VDC (nominal 24 VDC) Supervisory Current No additional current required, circuit appears as standard end-of-line (EOL) NAC loading Alarm Current Reference RAC Current NAC Current 0.5 A 0.845 A 1.25 A 2.14 A 0.75 A 1.28 A 1.5 A 2.56 A 0.87 A 1.5 A 1.75 1A 1.71 A 2A (RAC current = actuator current) RAC Current NAC Current 3A Wire Connections Screw terminals for input and output wiring, 18 to 12 AWG wire (0.82 mm2 to 3.31 mm2) IDNet Wiring Distance Reference Up to 10,000 ft (3048 m) total Class B wiring distance including T-Taps Up to 2500 ft (762 m) from the IDNet source module Compatible with Simplex 2081-9044 Overvoltage Protectors Dimensions See installation reference on page 8 Operating Temperature 32° to 120° F (0° to 49° C) indoor operation only Operating Humidity Range 10 to 90% RH at 90° F (32° C) Coil Supervision Module 2081-9046 Construction Epoxy encapsulated Dimensions 1-3/8” W x 2-7/16” L x 1-1/16” H (34 mm x 62 mm x 27 mm) Wiring 18 AWG (0.82 mm2) wire leads, color coded Current Rating 2 A Maximum; internally fused at 3 A, non-replaceable Compatible UL Listed Valves and Actuators MFG. ANSUL Model Number *AUTOMAN II-C Assembly; solenoid 17728; coil 25924 AUTOMAN II-C Explosion-Proof Releasing Device; solenoid 31492; coil 31438 *AUTOMAN II-C Assembly; solenoid 68739; coil 25924, Solenoid Electric Actuator; solenoid 73111; coil 73097 Coil Details MFG. 12 VDC, 458 mA 8210A107 (097617-005D coil) 1/2” NPS, 5/8” orifice, 24 VDC 24 VDC, 467 mA 12 VDC, 458 mA Model Number 8210G207 (238310 coil) 1/2” NPS, 1/2” orifice ASCO 8211A107 (097617-005D coil) 24VDC 24 VDC, 1 A HV2628571 (23810 coil) N.C. 1/2” NPS, 1/2” orifice 9 VDC max, 450 mA LP CO2 w/ASCO solenoid 422934, 24 VDC, 442 mA HV2648581 (23810 coil) N.O. 1/2” NPS, 1/2” orifice R8210A107 (097617-005D coil) 1/2” NPS, 5/8” orifice T8210A107 (097617-005D coil) 1/2” NPS, 5/8” orifice LP CO2 double action solenoid 430948 LP CO2 3-way selector valve solenoid 433419 Electric Actuator 24 VDC solenoid 570537 24 VDC, 438 mA ECH Electrical Control Head (551201) *CV90 HF Electric Actuator 73327; may use 73606 in-line resistor for 12 VDC 24 VDC, 438 mA PyroChem 24 VDC, 250 mA Explosion-Proof Electric Actuator (570147) Removable Electric Actuator (570209) 0.2 A 71395SN2ENJ1NOH111C2 (Skinner coil H111C2) 1/4”, NPS, 1/16” 73212BN4TN00NOC111C2 (Skinner coil C111C2) 1/2”, 5-300 psi Skinner 73212BN4TNLVNOC322C2 (Skinner coil C322C2) 1/2”, NPS, 0.92 A, 250 psi 73218BN4UNLVNOH111C2 (Skinner coil H111C2) 73218BN4UNLVNOC111C2 (Skinner coil C111C2) 1/2”, NPS, 5/8 in. orifice * 12 VDC coils, either wire two in series for 24 VDC activation, or, if available from manufacturer, use series resistor 6 S4010-0005-3 2/2012 FM Approved Water Control Valves FM Group Manufacturer A Skinner Model Number LV2LBX25* Details 24 VDC, 11 W, 458 mA, 1/2 inch NPS, 1/2 inch orifice T8210A107 B ASCO R8210A107 24 VDC, 16.8 W, 700 mA, 1/2 inch NPS, 5/8 inch orifice 8210A107 D ASCO 8210G207 24 VDC, 10.6 W, 440 mA, 1/2 inch NPS, 1/2 inch orifice 73218BN4UNLVNOC111C2* 24 VDC, 10 W, 420 mA, 1/2 inch NPS, 5/8 inch orifice 73212BN4TN00N0C111C2 24 VDC, 10 W, 420 mA, 1/2 inch NPS, 5/8 inch orifice; 5-300 psi rated working pressure E Skinner F Skinner 73212BN4TNLVNOC322C2 24 VDC, 22 W, 1/2 inch NPS, 920 mA, 250 psi (1725 kPa), 1/2 inch orifice G Skinner 71395SN2ENJ1NOH111C2 24 VDC, 10 W, 420 mA, 1/4 inch NPS, 1/16 inch orifice, 250 psi (1725 kPa) rated working pressure I Vitaulic Series 753-E solenoid valve 24 VDC, 8.7 W, 1⁄2 inch NPS, 364 mA, 300 psi (2069 kPa), 1⁄2 inch orifice J Viking 11591 and 11592 Normally closed (NC) 11595 and 11596 Normally open (NO) K Viking 11601 and 11602 NC solenoid valve, 24 VDC, 9 W, 1⁄2 inch NPS, 250 psi (1725 kPa), 6.2 Cv Explosion proof solenoid valves, 24 VDC, 10 W, 1⁄2 inch NPS, 300 psi (2069 kPa), 4.1 Cv * For new applications, LV2LBX25 has been replaced by model number 73218BN4UNLVNOC111C2. 7 S4010-0005-3 2/2012 Suppression Release Peripheral Installation Reference Diagram 2975-9227 Box, red with white lettering (supplied with 4090-9006) Door hinges on left and lifts off for access 4 Knockouts, one each side Door height 8-1/8" (206 mm) Door screw fastener 4090-9812 LED indicator option (supplied with 4090-9006) Door depth 1/2" (13 mm) Box depth 4" (102 mm) Door width 6-1/8" (156 mm) Box depth with door 4-1/16" (103 mm) NAC + 4090-9005 Suppression Release Peripheral assembly (supplied with 4090-9006) NAC - Box height 8" (203 mm) IDNet- RAC + RAC - IDNet+ ON 1 2 3 4 5 6 7 8 IDNET SUPPRESSION RELEASE PERIPHERAL ASSY 566-104 Box width 6" (152 mm) TYCO, SIMPLEX, and the product names listed in this material are marks and/or registered marks. Unauthorized use is strictly prohibited. Tyco Fire Protection Products • Westminster, MA • 01441-0001 • USA www.simplexgrinnell.com S4010-0005-3 2/2012 © 2012 Tyco Fire Protection Products. All rights reserved. All specifications and other information shown were current as of document revision date and are subject to change without notice.
© Copyright 2018 ExploreDoc